The City of Pasadena power plant had a major corrosion issue due to chemical attack that required a complete retube of a 2200 Ton McQuay Condenser. The chemical also eroded some of the steel off the condenser tube sheets and heads.
We furnished all of the labor and replacement tube materials and completely retubed the condenser. Once we finished the retube, we grit blasted and coated the condenser and heads with Belzona 1321 and also installed sacrificial anodes. We provided them with a 5 year warranty. Now the condenser stays cleaner, with no rust and we continue to provide ongoing inspection services to insure that they do not have this type of mishap again.
Please provide us your name, phone number, email address, location of equipment, model and serial# of equipment that you want us to help you with. Please provide a brief description of what you need or problems you are having with your equipment.