Trane CVHE 1250 - 1 America Plaza San Diego
Before and after pictures of a Trane 1250 ton Centrifugal that had pin holes in the evaporator shell. This unit was losing refrigerant and taking on air. This was due to poor lagging/insulation coverage. Our technicians grit blasted the entire shell, filled the pits and pin holes with an epoxy product called liquid metal, then we completely over coated the entire shell with 100% epoxy Enecon ceramalloy coating.
Please provide us your name, phone number, email address, location of equipment, model and serial# of equipment that you want us to help you with. Please provide a brief description of what you need or problems you are having with your equipment.