Trane CVHF 1050
Trane CVHF-1050 condenser with internal pitting. Cause, tower fill media stuck in tubes causing under deposit corrosion. Some of These tubes had to be plugged of to prevent failure.
Please provide us your name, phone number, email address, location of equipment, model and serial# of equipment that you want us to help you with. Please provide a brief description of what you need or problems you are having with your equipment.