York Project - Fresno, CA
York YK condenser, Fresno CA. This was supposed to be a routine ECA inspection. We found severe mechanical wear at the supports area from the unit vibrating well beyond design. The unit is mounted on a steel floor in a trailer and the owners run it at very low loads causing it to cycle surge. To make matters worse the unit was short of refrigerant causing a surge. This accelerated vibration which in turn wore the tubes out and began to cause them to cave in. We plugged them off to save the unit, later we did a partial retube to discover several had failed after we had plugged them off. They were very fortunate.
Please provide us your name, phone number, email address, location of equipment, model and serial # of equipment that you want us to help you with. Please provide a brief description of what you need or problems you are having with your equipment.